Pool Frog Leap Infuzer Installation Instructions
Learn how to install a Pool Frog Leap Mineral Infuzer to your existing filter system by following our step by step guide.
The FROG Leap Infuzer should always be installed between the filter return line and the return jet of the pool (or outlet of heater and return jet of pool if applicable). Never install FROG Leap Infuzer before the heater. Any additional sanitizing equipment that is installed with FROG Leap Infuzer must be installed after FROG Leap Infuzer (never before) on the return line to the pool.
INCLUDED WITH FROG Leap Infuzer
Pipe Thread Tape or Sealant
One 6” X 1 ½” TBE PVC Nipple
One Hose Adapter 1 ½” X 1 ½” X 1 ¼” (provided with filter)
One section of 1 ½” Flex Hose (provided with filter)
One hose clamp (provided with filter)
- Corrosion Resistant Check Valve
- 4-8 psi Back Pressure (To avoid over or under chlorination, replace eye ball fittings in the return jet to a smaller or larger size to adjust back pressure.)
Apply pipe thread tape or sealant to each threaded end of nipple.
Screw one end of nipple into the filter return. Hand tighten. Finish tightening by turning 1 to 2 revolutions with wrench.
Screw either side of FROG Leap Infuzer on to open nipple end until upright and secure.
Apply pipe thread tape or sealant to threaded end of hose adapter.
Screw adapter into the other side of FROG Leap Infuzer. Hand tighten. Finish tightening by turning 1 to 2 revolutions with wrench. DO NOT OVER TIGHTEN.
Attach return section of hose to the adapter with clamp. Tighten clamp with screwdriver.
If using a FROG Leap Torpedo Pac, installing a corrosion resistant check valve is recommended.